An Intumescent Strip Sealant 20mm x 3mm which can provide 60 minutes resistance to the passage of fire when used to glaze fire rated glass into internal doors and timber screens. Please ask our customer care team to send you a copy of our Certifire certificate CF297 for clear and concise applications for Firestrip® 30 and Firestrip® 60 and new increased glass sizes. BWF Certifire approved (CF297) intumescent glazing tape. Tested to EN 1634: Part 4 and EN 1364: Part 1.
Provides 60 minutes’ fire resistance to the passage of fire in timber doors and screens. Can be used with a wide variety of insulating and non-insulating fire glass types, please refer to the product data sheet for further information.
Application temperature range: +5°C to +30°C
Shelf life: 12 months when stored flat in original packaging in cool, dry conditions.
Surface preparation: All surfaces should be clean, dry and free from frost, grease and loose materials.
Application: Secure one set of glazing beads to act as a rebate if the opening is not already rebated. Pins or screws should be angled at 45°. Apply Firestrip® 60 on the paper along the rebate upstand of the top rebate by running the edge of the backing paper along the rebate platform so that the strip comes up to the sightline. For larger rebates it may be necessary to lift the paper above the platform to ensure that the Firestrip® 60 comes up to the sightline. Repeat the application to the sides and then the bottom rebate. Remove backing paper. Butt the corner joints, do not overlap. Position setting blocks. Centralise glass in frame on setting blocks. Press firmly around the edge of the glass to ensure that contact with the surface of Firestrip® 60 is achieved. Apply Firestrip® 60 to the glass in the same way as it was applied to the upstands by running the edge of the paper along the rebate platform or alternatively direct to the beads. Remove the backing paper. Bed the beads to the Firestrip® 60 by applying pressure to obtain good contact between the strip and the bead. Fix the beads with pins or screws in accordance with the design requirements of the installation. Pins or screws should be angled at 45° to pass beneath the glass. Trim off any Firestrip® 60 above the sight line with a sharp knife.
Sign up to receive the latest information from Hodgson Sealants
From 1st March the minimum order spend to receive free delivery will be increasing to £100 Dismiss